ClemensYour products are used in industrial refurbishment projects here in Europe and enjyo excellent reputation.
TamasWe are using some of your products and they are excellent!
AngeloYour HT18V-I works perfectly for my project.
Automatic Motion Detected Illuminated On Off Switch Remote Control For Highbay Light
|Place of Origin||China|
|Minimum Order Quantity||100PCS|
|Packaging Details||Bubble pack, paper flat, outer carton.|
|Delivery Time||1-3 days for sample order, 1-2 weeks for bulk order|
|Payment Terms||L/C, T/T, Western Union|
|Supply Ability||200,000pcs per month|
|Input Voltage||120~277VAC 50Hz60Hz||Detection Area||25%/50%/75%/100%|
|Stand-by Power||≤0.5W||Hold Time||5s/30s/1min/3min/5min/10min/20min/30min|
|Appearance||Black Translucent Shell||Operating Temperature||-20°C~+60°C|
|Mounting Height||8-15m/26.25-49.2ft (ceiling Mounted)||IP Rating||IP20|
microwave motion detector,
light on off sensor
Illuminated On Off Function Automatic Motion Detected Remote Control For Highbay Light
1. Automatic ON/OFF control with daylight sensor.
2. Microwave frequency would be 5.8GHz±75MHz.
3. Optional detection range, holdtime and daylight threshold.
4. Set the parameters which you want by remote controller.
5. 15m High mounted,for LED highbay.
6. Loop in and loop out for easy installation.
7. IP 20 with 5 years warranty.
|Input voltage||120-277VAC 50/60Hz|
|Switching capacity|| 120V,Max,200W(Control gear); Max.400W(Incandescent lamp) |
277V,Max,400W(Control gear); Max.800W(Incandescent lamp)
|Daylight threshold||2Lux/10Lux/30Lux/50Lux/80Lux/120Lux/ Disable|
|Mounting height||8-15m/26.25-49.2ft (ceiling mounted)|
|Detection range|| |
Radius, 3-6m/9.84-19.68ft (ceiling mounted)
|Operating temperature||Ta: -20°C+60°C|
|IP rating|| |
6-pole pluggable clamp terminal (L,N,PG,PG,N,L') for 1.5mm² cable.
Detection area Daylight sensor Hold time 10-15M Highbay
ON/OFF Control Warranty 5 years Remote Control
This figure indicates the maximum distance at the highest mounting height with 100% sensitivity.
Typical installation height 8-15m.
With remote control to set all parameters.
With six poles to easily connect with LED driver and power supply.
6-pole pluggable clamp terminal(L,N,N,L')for 1.5mm² cable.
With four installation hole at back, easily fixed to the lighting fixture for end user.
1. Automatically ON/OFF function:
Light on when detect movement and off after people leave at night. Applications: Corridor, Staircase.
With sufficient daylight, With insufficient daylight, After the last detection and
even when motion detected, when motion detected, light ON. the present hold time
light remains OFF. elapsed, light OFF.
2. No daylight function
The daylight threshold is set to "Disable".
Light on when detect movement, After people leave, Light off after hold time.
Applications: Dim places such as Basement Parking, Underpass.
When motion is detected, After people leave the detection After the last detection and
the sensor will switch on the area, light remains 100% the present hold time
light to 100% brighteness. brightness within hold time. elapsed, light OFF.
1.Microwave can penetrate walls or glass thinner than 20cm and attenuate if thicker than 20cm.
2. The driver voltage shall be stable and float within 10%.
3. Detection area will be affected by speed of motion, mounting height and movement volume.
4. Conduct test on sunny days without the lampshade which will affect the tested lux value.
1.Microwave sensor can be installed in any lamp except the one with full metal shell.
2.The detected surface cannot be shielded by metal objects.
3.Make sure the microwave module is completely exposed outside.
4.The detection surface of the sensor module shfall be installed facing the detection area.
5.Should be kept away from driver to avoid interference genaration and lamp flashing.
6.Wiring must be strictly in accordance with the wiring diagram to avoid short circuit.
1.Suitable for indoor installation to avoid false triggering due to external factors such as rain,wind or tree swing.
2.Shall not be installed in the place with all four metal shelters and small space(such as galvanized-iron roof).
3.Shall note be mounted installation,so as to avoid false trigger caused by the lamp itself shaking.
4.Shall not be installed next to large operating machines such as ventilator/ceiling fan to avoid fase triggering caused by machine vibration.