|Place of Origin:||China|
|Certification:||CE TUV RED SAA|
Payment & Shipping Terms:
|Minimum Order Quantity:||100PCS|
|Packaging Details:||Bubble pack, paper flat, outer carton.|
|Delivery Time:||1-3 days for sample order, 1-2 weeks for bulk order|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||200,000pcs per month|
220V 240VAC Ceiling Light Motion Sensor Driver Isolated Max 28W Power
220-240VAC 28W LED Driver & Sensor 2-in-1 Isolated Solution with 5.8GHz Microwave Motion Detector For Ceiling Light
1. Input current 0.14-0.2A max. with power of 33W.
2. Optional Output current of 0.45A/0.55A/0.60A/0.70A for different projects.
3. Output LED power from 11W to 28W max.
4. Optional detection area, hold time, stand-by dimming level, stand-by period and daylight threshold.
5. Max. mounting height x detection range: 6M x 14M.
6. Empty Load voltage of 55V max.
7. Efficiency of 85%
8. Abnormal protection SCP: Auto recovery, OVP, OCP, OTP
|Input voltage||220~240VAC 50/60Hz|
|Input current||0.2-0.14A Max|
|Input power||33W Max|
|Hold time||5s/90s/ 5min/10min|
|Daylight threshold||2Lux /10Lux /50Lux/Disable|
|Stand-by period||0s/10s/10min /+∞|
|Stand-by dimming level||10%/30%|
|Output LED current||0.45A/0.55A/0.6A/0.7A|
|Output LED voltage||24-42V/24-42V/24-42V/24-40V|
|Output LED power||11-19W/13-23W/14-25W/17-28W|
|Empty load voltage||≤55V|
|Operating temperature||Ta: -20°C+50°C Tc: 80°C|
|Abnormal protection||SCP:Auto recovery,OVP,OCP,OTP|
|Safety standard||EN61347-1 EN61347-2-13 EN60598-1|
|Life time||30,000 hours|
This figure indicates the maximum distance at the highest mounting height with 100% sensitivity.
Typical installation height 2.5-6m.
With eight DIP switch poles to set all parameters
With two DIP switch poles to choose different output current
With two installation hole, easily fixed to the lighting fixture for end user.
DIP Switch Setting
Detection area Hold-time Daylight threshold Stand-by period Stand-by dimming level
In this area, The period of Definition of the The period of light The definition of
movement will light keeping ambient brightness; keeping low output low output in the
be detected 100% brightness only when the before it's standby period.
and able to after moving ambient brightness completely
trigger the objects leave the is lower than the switched off. When
sensor. 100% detection area. preset specific lux it's preset as"∞“,
detection area amount, the sensor the light always
is also known will work; when it's keep at low output
as the strong preset as "disable", if no movement in
sensitvity. the sensor works the detection area
everytime it detects and doesn't turn off.
the ambient brightness.
1. Automatically ON/OFF function:
Light on when detect movement and off after people leave at night. Applications: Corridor, Staircase.
The daylight threshold is set to "2lux,10lux,50lux"
With sufficient daylight, With insufficient daylight, After the last detection and
even when motion detected, when motion detected, light ON. the present hold time
light remains OFF. elapsed, light OFF.
2. No daylight function
The daylight threshold is set to "Disable".
Light on when detect movement, After people leave, Light off after stand-by period.
Applications: Dim places such as Basement Parking, Underpass.
When motion is detected, After people leave the detection After the last detection and
the sensor will switch on the area, light remains 100% the present hold time
light to 100% brighteness. brightness within hold time. elapsed, light OFF.
3. Function Demo - Dimmable control/Corridor function
With sufficient daylight, With insufficient After last detection, After the stand-by
even when motion daylight, when motion light will be dimmed period, light OFF.
detected, light remains detected, light ON. down to the stand-by
OFF. dimming level (10% or
30%) after holdtime.
1.Microwave can penetrate walls or glass thinner than 20cm and attenuate if thicker than 20cm.
2. The driver voltage shall be stable and float within 10%.
3. Detection area will be affected by speed of motion, mounting height and movement volume.
4. Conduct test on sunny days without the lampshade which will affect the tested lux value.
|Contact Person :||Miss. Evelyn Chow|